To minimize land and water contamination by ensuring tank system installations meet minimum standards.
Required for new or replacement aboveground petroleum storage tank (AST) systems having an oil storage capacity of more than 660 gallons, or new or replacement underground or over-water piping systems.
Statute and Administrative Rules
Env-Wm 1402 Control of Aboveground Petroleum Storage Facilities
A complete application package including plans and specifications prepared and certified by a New Hampshire licensed professional engineer, must be submitted by the facility owner at least 45 days prior to commencing construction or installation of a new or replacement AST system.
One year from the date of issuance. An owner may request a waiver from the one year expiration period according to Env-Wm 1402.36.
Substantial design changes must be approved in writing by the design engineer of record and resubmitted for Aboveground Petroleum Storage Tank Program approval.
Status of Current Applications
Contact Bob Daniel at email@example.com or (603)271-0686.
Aboveground Petroleum Storage Tank Program
Adobe Acrobat Reader format. Download a free reader from Adobe.